Skip to Main Content
This paper describes a mathematical approach to the determination of the electrical load composition of a secondary network during cold-load re-energization. It is intended to answer two questions: What fraction of the normal steady-state demand must be restored at the time of re-energization in the most pessimistic case? What is the composition of this worse case restoration load?
Date of Publication: July 1983