Skip to Main Content
The 30-MJ energy storage coil for the Bonneville Power Administration requires a low-loss, cryostable conductor that is able to carry 4.9 kA in a field of 2.8 T and will maintain its properties over 108partial discharge cycles. The multi-level cable which satisfies these requirements has been extensively tested at various stages in its development and in its final form. Tests have been performed to determine the effect of manufacturing options on ac losses, low temperature electrical resistivity, stability, and fatigue resistance of the insulated conductor. This paper will concentrate on the stability and fatigue tests which have not previously been reported.