On Wednesday, July 29th, IEEE Xplore will undergo scheduled maintenance from 7:00-9:00 AM ET (11:00-13:00 UTC). During this time there may be intermittent impact on performance. We apologize for any inconvenience.
In the upcoming smart grid environment many more measurements will be available, which can be locally processed by the so-called substation state estimator (SSE). Distribution substations serve energy to a large set of feeders, each one delivering power to a certain number of secondary transformers. In this context, the SSE may have to deal with a huge network model, comprising several hundred or even thousand buses. Taking advantage of the weak electrical coupling existing among the set of feeders connected to the same or adjacent substations, a two-stage procedure is proposed in this paper to efficiently solve the SSE. In the first stage the overall SE is decomposed into f + s WLS subproblems (f and s being the total number of feeders and substations, respectively), which are then solved in a decoupled manner. The second stage, involving a linear WLS problem, consists of coordinating the solution provided by each subsystem (feeder or substation). The proposed solution scheme has a number of advantages, as shown by the case studies.